199 Total Reviews/files/dye-logo-250-130.jpg219-362-6251$1600 Lake Street, LaPorte IN
AC Cooling And Air Conditioning Systems Union Mills, Indiana
At Dye Plumbing & Heating, we install and service all brands of central air conditioning and cooling systems in Union Mills, IN. If you have an existing cooling system our trained staff can diagnosis your AC system and recommend terrific new high efficiency choices. We offer same day evaluation and prompt air conditioning installation services Union Mills, IN.
Let us help you decide how best to solve your air conditioning needs today.
Get Your Quote Today
Dye Plumbing & Heating AC Cooling And Air Conditioning Systems Union Mills, Indiana
Recent AC Cooling And Air Conditioning Systems Union Mills, Indiana by Dye Plumbing & Heating
5 Star Rating AC Cooling And Air Conditioning Systems Union Mills, Indiana Armstrong 4SCU13LE148P-5; Serial: 1619G10849 Series Outdoor Condensing Unit
- 13 SEER Efficiency Rating
- Insulated Sound Blanket To Help Reduce Operating Noise
- Safety Refrigerant Pressure Switches
Armstrong Model:HE35248A200A0000AP; Serial: 7119J07865 Series Indoor Evaporator Coil
SCOPE OF WORK:
1. Remove And Dispose Of The Existing Condensing Unit And Copper Refrigeration Line-set Piping.
2. Provide And Install The New Evaporator Coil In The Same Location Adapting To The Existing Furnace And Supply Air Duct Work.
- Install The Appropriate Piston Metering Device Supplied With The Outdoor Condensing Unit.
3. Provide And Install The New Outdoor Condensing Unit On A Field Supplied Composite Pad In The Same Location.
- Remove And Dispose Of The Existing Concrete Pad
- The Removal Of One Landscaping Block Will Be Necessary.
4. Adapt The New Condensing Unit To The Existing Electrical Circuit And Service Disconnect. Provide A New Electrical Whip And Replace The Existing Circuit Breaker With A New 50 AMP Breaker.
5. Provide And Install New Copper Refrigeration Piping From The Indoor Evaporator Coil To The Outdoor Condensing Unit.
6. Install New Condensate Drain Piping From The New Evaporator Coil Terminating To The Nearby Floor Drain.
7. Start The New Equipment And Check System Operation. UNION MILLS, IN 05-20-2020
5 Star Rating AC Cooling And Air Conditioning Systems Union Mills, Indiana Call For Boiler System Circulating Excessive Amounts Of Air. Isolated Boiler And Replaced Auto Air Vent, Relief Valve, And Drained Expansion Tank. Upon Re-pressurizing System Found Failed Fill-trol Expansion Tank. Replaced Fill-trol And Cycled Boiler From All Four Zones. Bled Accessible Radiation And Observed Unit Operation. All Radiation Is Heating Properly At This Time And Unit Cycles Off At 180° With A Pressure Of 15 PSIG. UNION MILLS, IN 03-18-2020